PE Series - Higher Power
Public Safety/BDA In-Building Coverage
An integral part of an in-building solution for emergency response radio coverage is the backup power system. NFPA codes relating to the autonomous operation and monitoring of the BDA power is quite stringent. These back up power enclosures were engineered to meet every aspect of NFPA 1221 and provide integrators configuration flexibility and rapid delivery directly to site, batteries included.
• NFPA compliant
• All required monitoring alarms
• Batteries included
• Choose capacity to match system requirements
• NEMA-4 UL listed enclosure
• Prewired for easy on-site connections
• Customization to meet local AHJ ‘s requirements
Input: 90 - 300V AC, 50/60 Hz.
DC: 48V, with 600 and 1200 Watt DC UPS
AC: 120V at 600 watts - see reverse for detailed specifications
Protections: Battery circuit breaker, DC output circuit breaker, NEMA enclosure, IP65 vents
NFPA 1221 Compliant Alarms (Form C, Dry Contact)
• AC fail
• Battery discharged to 30% of capacity
• Rectifier/Charger fail
Batteries Included: maintenance free, sealed valve regulated, lead acid, 160, 185, 370, and 600 AH capacity
Enclosure Size (H x W x D):
A: 50.23” x 25.5” x 34”
B: 78.23” x 25.5” x 34”
Enclosure A: 50” tall, NEMA-4, UL listed, welded aluminum with IP 65 battery vent and pad lockable door handles. Red powder coat wall mount.
Enclosure B: NEMA-4, UL listed, welded aluminum with IP 65 vent, pad lockable door handles. Red powder coat floor mount.
Battery string wiring: 8 AWG, two conductor with 5/16” ring battery terminals
Battery string circuit breaker: 30A
|Model||DC Voltage||DC UPS Power Watts||Battery A/H Capacity||Enclosure Size|
* Can be upgraded to larger enclosure, size B
Public Safety DAS Power PE Higher Power Series Enclosure Manual Library
The systems are defined with call-outs of the major features including the Sentinel DC Power System, system input breakers, battery breakers, alarms and batteries.
120 Volt AC, NFPA 1221 Integrated Power System
Voltage: 120V AC
DC Output: 600 Watts
Battery Back-Up: 185 - 370 Amp-Hour
PE Instruction ManualRequest Sentinel 48V DC, 600 Watt Power System Manual48-1000RM DC-AC Inverter Manual
48 Volt DC, NFPA 1221 Integrated Power System
Voltage: 48V DC
DC Output: 600 Watts
Battery Back-Up: 160 - 370 Amp-Hour
PE Instruction ManualRequest Sentinel 48V DC, 600 Watt Power System Manual